mel_F wrote:Hi James, I got a handy man in to do it and he screwed it straight in, no raw plug. The blind is very heavy and wide, and it seems to be fine.
Ventilator Nuaire - i reported this as broken, as the light was flashing on fault, apparently that's correct. It needed switching on/off to reset it and it works now. Still flashes fault though.
Great to be in !
JamesHunt wrote:Hi TDG1982
Mine was apparently part fixed.
I now have flow through some of my underfloor zones but not others. I didn't get any feedback either but emailed NHHG who sent over the United House site manager.
He seems to know his stuff (told me it was part working), had a fiddle but couldn't fix it, so there is someone else coming soon. I think my thermostats have been wired up incorrectly - they all click at a point where it seems they 'think' it is sub 10 degrees...
A lot of the problem lies in the fact that the different parts of the system (pipes, billing, thermostats) were installed by different sub-contractors, so one engineer can't guarantee the repair of the whole thing.
NikD wrote:Hey Oliver McC
I too have had an odd smell in the ensuite. It comes and goes at the moment. But as my ventilator has stopped working, I thought it might be that. Trying to organise for someone to look at it. Is your ventilator working?
For the latest local news and events direct to your inbox every Monday, you need our weekly email newsletter SE1 Direct.
7,000+ locals read it every week. Can you afford to miss out?
Read the latest issue before signing up